Team Howard Inc.
974 Rte 67
Ballston Spa, NY 12020
Office 518.885.8051 - www.teamhoward.com - Fax 518.885.8779
WIRING REQUIREMENTS FOR POINT-OF-SALE (POS) SYSTEM
ATTENTION: ELECTRICIAN AND OWNER
It is mandatory that the electrical line for the POS
be installed as followed.
Dedicated Line: This line must be three insulated
wired in conduit (or equal) capable of carrying 20 amps and running from the
Main panel box directly to the POS receptacles. No other
wires or receptacles are to be in or attached to this conduit.
Isolated Ground: The isolated ground wire must
run from the POS receptacles to a ground rod or water pipe. It must not be
connected to the common ground bar in the panel box.
Option 1 - From the receptacle to a driven ground stake of sufficient
length to provide a positive ground.
Option 2 - From the receptacle to a water pipe at the point
where the pipe enters the ground.
Receptacle: The receptacle must be an isolated
ground type. The recommended type is the Hubbell outlet (Levition is not
Upon completion of the line installation, notify Team Howard.
A service representative will then be scheduled to check wiring
for proper installation.
Failure to install the power line to the above specifications
may void the warranty of the POS components in your system.